There are 3 levels of sensitivity to smoke presence.


This parameter allows to activate excess temperature ...


Enclosure opening notification enabled +

Enclosure opening notification enabled and

Exceeding temp threshold notification enabled +

This parameter allows to activate visual indications


Enclosure opening notification enabled +

Enclosure opening notification enabled and

This parameter allows to activate sound signals...


Config of control frames in BASIC command class

This parameter defines which frames will be sent ...


BASIC ON frame is sent in case of smoke presence detection ...


BASIC OFF frame is sent in case of FIRE ALARM cancellation.


FIRE ALARM broadcast 2nd/4th Association Group...

FIRE ALARM broadcast 2nd/4th Association Group ...

A value other than 0 means that alarms are being ...


Associations in Z-Wave network security mode


Time interval between consecutive temperature reports.


The temperature report will only be sent if there is a difference ...


Temperature threshold for activating alarms


Time interval of signaling (visual indication/sound) excess ...


Lack of Z-Wave range indication interval

Time interval of signaling (visual indication/sound) lack of ...


Alarm Cancellation Delay


acoustic alarm inactive, visual alarm active

acoustic alarm active, visual alarm inactive

Alarm acoustic and visual signals


Type of alarm to 1st association group (SMOKE)


Forced Level of Dimming group 1


Interval between temperature  readings


Frame broadcast mode


Temperature measurement compensation


Z-Wave range test interval


Temperature alarm threshold


Smoke Sensor sensitivity


Black Box sensitivity level


Malfunction alarm


Temperature alarm


Lack of the Z-Wave range alarm


Low battery alarm


Temperature measurement compensation for report


Tamper alarm active, with cancellation option

Tamper alarm active, without cancellation option

Activates/inactivates temper switch alarm


value should be set to 1 if the module operates in Venetian Blind mode.


depending on mode, turning time or delay time


only in case of the main controller operation

Parameter influences the lamellas positioning in venetian blind mode


either Toggle switches or a single, momentary switch.


delay till auto turned off or auto gate close


Power threshold to be interpreted as reaching a limit switch.


Time period for the motor to continue operation.


set to 1 will enter calibration mode


0 no change, 1 extreme position


change that needs to occur  to trigger the power report


Time to the next report. Value of 0 means the reports are turned off.


Energy threshold to trigger report


if power and energy reports are to sent to the main controller


whether scenes or associations are activated by the switch keys


set automatically during the calibration


parameter is set automatically during the calibration process


Virtual value (percentage between 1% and 99%)


time required for switching. 0s - 25,5s


percentage of a dimming step at automatic control. 1-99


Dimming Step Timing at Automatic Control

Defines the time of a dimming step at automatic control


The parameter defines the percentage of a dimming step at manual control. 1-99


Defines the time of a dimming step at manual control.


All outputs are set to OFF upon power restore

Outputs set to previous state upon power restore

Saving state before power failure


Defines the setting of the timer


The parameter specifies the available functions.


Force auto-calibration without Fibaro Bypass

Force auto-calibration with Fibaro Bypass

Force calibration process


Dimmer operates on auto-calibration settings

Auto-calibration status (read-only parameter)

Operating mode of the Dimmer


Percentage value of power variation


Time of delay for power variation detection


Dimmer 2 will always set this brightness level.


Binary inputs type configuration


Dimmer 2 state synchronizes brightness level

Value sent to associated devices on single click

The value sent to associated devices on single click.


Device changes status on key status change

Allow changing [On-Off] bi-stable keys


Double-click set lighting at 100%


do not send when switching ON (single click)

do not send when switching OFF (single click)

Command frames sent in 2nd and 3rd assoc group

Actions not resulting in sending frames to assoc


Command frames sent in 4th and 5th assoc grp

Actions not resulting in sending frames to assoc grp


Key no. 2 controls the Dimmer additionally


Defines commands are sent as secure or non-secure


SCENE ID depends on the switch type configuration


Switch S1 and S2 buttons


The parameter defines the used control mode.


Load control mode recognized during auto-calibration


on/off mode disabled (dimming is possible)

on/off mode enabled (dimming is not possible)

Mode for connecting non-dimmable light sources


Dimmability of the load (read only)


Time required to warm up the filament of halogen bulb.


No auto-calibration of the load after power on

Auto-calibration performed after first power on

Auto-calibration performed after each power on

Auto-calibration after pwr up or load error

Auto-calibration after pwr on or load error

Determines trigger of auto-calibration procedure


Behaviour of the Dimmer after overload or surge


Brightness level correction for flickering loads

Duration of brightn level correction for flickering


Defined value turns off load


The parameter specifies the response to an alarm.


Time alarm state cancelled


(load power consumption too high)


(no load, load failure, burnt out bulb)


(short circuit, burnt out bulb causing overcurrent)


(Dimmer output overvoltage)


Critical temperature/VOLTAGE DROP alarm report


Pwr level change resulting in power report sent


Periodic active power and energy reports

Time period between consecutive reports


Energy level change resulting in energy report sent


Reports include power/energy used by device


measurement based on the standard algorithm

approximation based on the calibration data

approximation based on the control angle

Calculation of active power


Approximated power at the maximum brightness level


There are 3 levels of sensitivity to smoke presence.


This parameter allows to activate excess temperature ...


This parameter allows to activate visual indications


This parameter allows to activate sound signals...


This parameter defines which frames will be sent ...


BASIC ON frame is sent in case of smoke presence detection ...


BASIC OFF frame is sent in case of FIRE ALARM cancellation.


A value other than 0 means that alarms are being ...


Associations in Z-Wave network security mode


Time interval between consecutive temperature reports.


The temperature report will only be sent if there is a difference ...


Temperature threshold for activating alarms


Time interval of signaling (visual indication/sound) excess ...


Time interval of signaling (visual indication/sound) lack of ...